3.0 HP, R448A/R404A/A2L, 220V AC Indoor Condensing Unit

Boyard
Fri, 03 Jan 2025 02:35:58 +0000

220V AC Indoor Condensing Unit refrigerating parts r22 r404a condenser unit,Compact Size.?Horizontal condensing unit are suitable for self-contained showcase thanks to their low height.

Low noise & vibration.?In the rotary type, noise and vibration is largely reduced compared with the reciprocating compressor. Therefore noise generated by the unit can be reduced.

High reliability.?High reliability is achieved due to high-quality material and high-accuracy parts.

High efficiency.?Using high efficiency rotary compressor and motor, energy saving.

Wide Evaporating temperature range.?Evaporating Temperature is from -5 degree to -40 degrees.

Low height.?The total height of the Horizontal condensing unit is not more than 275mm

?Technical Data of Vertical Series Condening Uint
?Model | HQXD-13KBI | HQXD-16KBI | HQXD-23KBI | HQXD-30KBI | HQXD-36KBI | HQSD-456KBI | HQSD-456MBI
?Nominal Input（W） | 800 | 980 | 1500 | 1900 | 2080 | 2450 | 2450
?Power Supply | 1PH 220V 50Hz | 1PH 380V/50Hz
Refrigerant | R404A/R448A/R449A/R452A/R455A
?Refrigerant Max.（Kg） | 1.5 | 2.0 | 2.5 | 3.0 | 3.0 | 3.5 | 3.5
?Start-Up Current (A) | 26 | 30 | 40 | 52 | 60 | 65 | 65
② Max Running Current (A) | 5.1 | 6.9 | 9 | 11.2 | 12.3 | 14.0 | 14.0
?Evap.Temp(℃) | -40～-5

Ambient Temp(℃)

0～43℃
（The environmental temperature under 10℃, Increase the condensation temperature control）

?Compressor（Model） | QXD-13K | QXD-16K | QXD-23K | QXD-30K | QXD-36K | TXSD456KS | TXSD456F
Condebser | ?Style | ?? Copper tube fin condenser or microchannel condenser
Fam Motor | （mm）Diameter Quantity | 250*1 | 250*1 | 300*1 | 350*1 | 350（400*1） | 400*1 | 400*1

(m3/hr)
Air Flow

1100

1100

1750

2670

2670

3750

3750

(mm)
Pipe

Gas Inlet Diam

φ12.7(1/2″)

?Liquid Outlet | φ9.53(3/8″)

(mm)
Out Dimension

(mm) Length

360

360

480

560

620

620

620

(mm) Width | 600 | 600 | 550 | 560 | 560 | 560 | 560
(mm) Height | 340 | 340 | 375 | 400 | 410 | 500 | 500

（W）
Capacity

(℃) Evap Temp

?Ambient Temp:32℃

-40 | 390 | 515 | 660 | 860 | 970 | 1100 | 1100
-35 | 535 | 670 | 855 | 1065 | 1240 | 1415 | 1415
-30 | 655 | 775 | 960 | 1295 | 1450 | 1790 | 1790
-25 | 735 | 925 | 1210 | 1520 | 1710 | 2160 | 2160
-20 | 920 | 1170 | 1465 | 1925 | 2200 | 2695 | 2695
-15 | 1105 | 1495 | 1740 | 2285 | 2690 | 3090 | 3090
-10 | 1385 | 1675 | 2200 | 2710 | 3225 | 3935 | 3935
-5 | 1650 | 1910 | 2535 | 3030 | 3850 | 4730 | 4730

Wiring
Capacity

Protector

(A)
Rated Current

10

15

20

20

20

20

20

(mA)
Leak Current

30

30

30

30

30

30

30

(mm2)
Diameter

L≤10m

2.5

2.5

4.0

4.0

4.0

4.0

4.0

10＜L≤20m | 2.5 | 2.5 | 6.0 | 6.0 | 6.0 | 6.0 | 6.0
20＜L≤30m | 2.5 | 2.5 | 6.0 | 6.0 | 6.0 | 6.0 | 6.0