3HP, R448A/R404A/A2L, 220V AC Indoor Condensing Units

Boyard
Wed, 14 Sep 2022 03:05:06 +0000

Model No. | HQHD-23KNP01 | HQHD-30KNP01 | HQHD-36KNP | HQSD-456KNP
Nominal Input(W) | 1350 | 1700 | 1900 | 2300
Power Supplier | 1PH 220～240V 50Hz
Refrigerant | R404A
Refrigerant Max.(KG) | 2.0 | 3.0 | 3.0 | 3.5
Start-Up Current(A) | 38 | 42 | 50 | 65
Max Running Current(A) | 8.2 | 10.0 | 11.0 | 13.5
Evap.Temp. Range | ?-40～-5℃
Ambient.Temp.Range | ?10～43℃
Compressor | QHD-23K | QHD-30K | QHD-36K | THSD456KS 1A
Condenser | Fan Motor | Specification | /
Diameter*Quantity
Air Flow(m3/hr)
Pipe | Gas Inlet Diam. | φ12.7（1/2″）
Gas Outlet Diam. | φ9.53（3/8″）
Out Dimension | (mm)Length | 790 | 940 | 940 | 1180
(mm)Width | 260 | 260 | 260 | 260
(mm)Height | 260 | 260 | 260 | 275
(W)Capacity | Evap. Temp. | Ambient Temp.32℃
-40 | 660 | 860 | 970 | 1100
-35 | 855 | 1065 | 1240 | 1415
-30 | 960 | 1295 | 1500 | 1790
-25 | 1210 | 1705 | 1885 | 2260
-20 | 1465 | 1925 | 2200 | 2695
-15 | 1740 | 2285 | 2690 | 3180
-10 | 2200 | 2710 | 3225 | 4055
-5 | 2535 | 3030 | 3850 | 4870
Wiring Capacity | Leak Protector | Rated Current(A) | 20 | 20 | 20 | 25
Leak Current(mA) | 30 | 30 | 30 | 30
线径(mm?) | L≤10m | 2.5 | 4.0 | 4.0 | 4.0
10＜L≤20m | 2.5 | 6.0 | 6.0 | 6.0
20＜L≤30m | 2.5 | 6.0 | 6.0 | 6.0