2.0 HP, R448A/R404A/A2L, 220V AC Indoor Condensing Unit

Boyard
Fri, 03 Jan 2025 02:35:58 +0000

220V AC Indoor Condensing Unit r404a refrigeration condensing units,Compact Size.?Horizontal condensing unit are suitable for self-contained showcase thanks to their low height.

Low noise & vibration.?In the rotary type, noise and vibration is largely reduced compared with the reciprocating compressor. Therefore noise generated by the unit can be reduced.

High reliability.?High reliability is achieved due to high-quality material and high-accuracy parts.

High efficiency.?Using high efficiency rotary compressor and motor, energy saving.

Wide Evaporating temperature range.?Evaporating Temperature is from -5 degree to -40 degrees.

Low height.?The total height of the Horizontal condensing unit is not more than 275mm.

Technical Data of HQHD Series Condening Uint（Condenser big）
?Model | HQHD-16KBI24 | HQHD-23KBI22 | HQHD-30KBI22 | HQHD-36KBI22 | HQHD-456KBI22
① Nominal Input（W） | 900 | 1320 | 1680 | 1900 | 2300
?Power Supply | 1PH 220～240V 50Hz
?Refrigerant | R404A
?Refrigerant Max.（Kg） | 1.5 | 2.0 | 3.0 | 3.0 | 3.5
Start-Up Current (A) | 27 | 38 | 42 | 50 | 65
② Max Running Current (A) | 6.0 | 8.2 | 10.0 | 11.0 | 13.5
Evap.Temp(℃) | -40～-5℃

Ambient Temp(℃)

10～43℃

（The environmental temperature under 10℃, Increase the condensation temperature control）

?Compressor（Model） | QHD-16K | QHD-23K | QHD-30K | QHD-36K | THSD456KS 1A
Condenser | ?Style | 4排5.5环 | 4排5.5环 | 4排5.5环 | 5排5.5环 | 5排5.5环

Fam Motor

（mm）
Diameter Quantity

φ254*2
(16W*2)

φ254*2
(16W*2)

φ254*3
(16W*3)

φ254*3
(16W*3)

φ254*3
(16W*4)

(m3/hr)
Air Flow

840*2

840*2

840*3

840*3

840*4

(mm)
Pipe

?Gas Inlet Diam

φ12.7(1/2″)

?Liquid Outlet | φ9.53(3/8″)

(mm)
Out Dimension

(mm) Length

680

830

1350

1350

1350

(mm) Width | 520 | 520 | 540 | 540 | 540
(mm) Height | 285
（Kg）Weight | 37.5 | 40.6 | 58.5 | 60.3 | 66.3

（W）
Capacity

(℃) Evap Temp

?Ambient Temp:32℃

-40 | 515 | 660 | 930 | 970 | 1100
-35 | 670 | 855 | 1165 | 1240 | 1415
-30 | 775 | 960 | 1395 | 1571 | 1790
-25 | 985 | 1210 | 1705 | 1980 | 2260
-20 | 1170 | 1463 | 1925 | 2360 | 2695
-15 | 1540 | 1790 | 2350 | 2770 | 3180
-10 | 1725 | 2265 | 2790 | 3320 | 4055
-5 | 1965 | 2610 | 3120 | 3965 | 4870

Wiring
Capacity

Leak Protector

(A)
Rated Current

15

20

20

20

25

(mA)
Leak Current

30

30

30

30

30

(mm2)
Diameter

L≤10m

2.5

2.5

4.0

4.0

4.0

10＜L≤20m | 2.5 | 2.5 | 6.0 | 6.0 | 6.0
20＜L≤30m | 2.5 | 2.5 | 6.0 | 6.0 | 6.0