220V 50/60Hz Horizontal Frequency Conversion Unit HQSD-360KBI40

Boyard
Tue, 28 May 2024 01:55:12 +0000

Horizontal Frequency Conversion Unit Technical Data
Model | HQSD-210KBI40 | HQSD-285KBI40 | HQSD-360KBI40
Nominal Input（W） | 1200 | 1550 | 1950
Power Supply | 220V 50/60?Hz
Refrigerant | R404A or Equivalent
Refrigerant Max.（Kg） | 1.8 | 2.5 | 3.5
Max Running Current (A) | 6 | 10.5 | 13.5
Evap.Temp(℃) | -40～-5℃
Ambient Temp(℃) | 10～43℃
Compressor（Model） | JHSD150Z312 | KHSD203Z312 | KHSD300Z312
Condenser | Style | Copper tube fin condenser or microchannel condenser
Fan Motor | （mm）Diameter Quantity | φ230*2 (EC fan) | φ230*3 (EC fan) | φ230*3 (EC fan)
(m3/hr) Air Flow | 730*2 | 730*3 | 730*3
(mm) Pipe | Gas Inlet Diam OD | φ12.7(1/2")
Liquid Outlet OD | φ9.53(3/8″)
(mm) Out Dimension | (mm)Length | 790 | 940 | 1145
(mm)?Width | 600 | 620 | 600
(mm) Height | 251
(Kg）Weight | 33.5 | 47 | 53
（W） Capacity | (℃) Evap Temp | Ambient Temp:32℃? ?Sub-cooling 0℃
-40 | 590 | 840 | 990
-35 | 720 | 1040 | 1260
-30 | 910 | 1250 | 1480
-25 | 1150 | 1500 | 1750
-20 | 1410 | 1890 | 2250
-15 | 1700 | 2240 | 2750
-10 | 2000 | 2650 | 3300
-5 | 2320 | 2950 | 3930
Wiring Capacity | Leak Protector | (A) Rated Current | 15 | 20 | 20
(mA) Leak Current | 30 | 30 | 30
(mm2) Diameter | L≤10m | 2.0 | 4.0 | 4.0
10＜L≤20m | 2.5 | 6.0 | 6.0
20＜L≤30m | 2.5 | 6.0 | 6.0
①Refrigerating capacity test condition；②The biggest running current test condition。
(GB/T 21363-2008)TEST CONDITION:
| TEST CATION | AMBIENT TEMP. | ? ? ? ? ? ? ? ?RETURN GAS TEMP. | ? ? ? ? ? ? ? ? EVAP. TEMP.
① | STANDARD TEST CONDITIONS | 32℃ | 18℃ | ?-7℃
② | OVERLOAD? RUNNING | 43℃ | 18℃ | 0℃