13.0 HP, MBP, R448A/R404A/A2L, 380V AC Outdoor Remote Condensing Unit

Boyard
Wed, 11 Feb 2026 05:25:53 +0000

BYGF-130-ZBM-RMDP
Power Supply | HP Compressor | Refrigerant | Cooling Capacity(W) | Evap. Temp.(℃) | Compressor Model | Product Dimension(mm)
Te=0℃, Tsuc=18℃, Ta=32℃ | Te=-20℃, Tsuc=18℃, Ta=32℃
3PH 380V 50Hz | 13.0 HP | R448A/R404A/A2L | 28050 | 13750 | -20～10 | ZB95KQE | 1400*810*1230

2-13 HP R448A/R404A/A2L MBP Fixed Frequency 380V Outdoor Refrigeration Unit
? Model | BYGF-020-ZBM-SMDP | BYGF-030-ZBM-SMDP | BYGF-040-ZBM-SMDP | BYGF-050-ZBM-SMDP | BYGF-060-ZBM-SMDP | BYGF-070-ZBM-SMDP | BYGF-080-ZBM-RMDP | BYGF-100-ZBM-RMDP | BYGF-130-ZBM-RMDP
Power Supply | 3PH 380V 50Hz
HP Compressor | 2 HP | 3 HP | 4 HP | 5 HP | 6 HP | 7 HP | 8 HP | 10HP | 13HP
Refrigerant | R449A / R448A / R454C / R455A / R404A
Evap. Temp.(℃) | -20～10
Ambient Temp.(℃) | -15～45
Compressor Model | ZB15KQE | ZB21KQE | ZB29KQE | ZB38KQE | ZB45KQE | ZB48KQE | ZB58KQE | ZB76KQE | ZB95KQE
Product Dimension(mm) | 1015*420*850 | 1015*420*1250 | 1000*810*1230 | 1400*810*1230
Installation Dimension(mm) | 580*385 | 450*760 | 900*760

R449A Cooling
Capacity（W）

Evap. Temp.(℃)

Test Conditions：GB/T 21363-2018??? Ambient Temp.:32℃?? Subcooling Temp.:0℃?? Suction Temp.:18℃

-20 | 2090 | 3250 | 4450 | 5600 | 6600 | 7200 | 8350 | 11300 | 13750
-15 | 2570 | 3950 | 5300 | 6700 | 7900 | 8650 | 10300 | 13950 | 17000
-10 | 3120 | 4650 | 6350 | 8000 | 9350 | 10300 | 12350 | 16250 | 20450
-5 | 3720 | 5550 | 7500 | 9450 | 11150 | 12150 | 17450 | 19500 | 24150
0 | 4410 | 6500 | 8800 | 11150 | 13000 | 14300 | 17200 | 22950 | 28050
5 | 5110 | 7550 | 10200 | 12900 | 15250 | 16700 | 19950 | 26650 | 32600