6.0 HP, LBP, R448A/R404A/A2L, 380V AC Outdoor Remote Condensing Unit

Boyard
Tue, 24 Feb 2026 04:07:30 +0000

BYGF-060-ZSL-SMDP
Power Supply | HP Compressor | Refrigerant | Cooling Capacity(W) | Evap. Temp.(℃) | Compressor Model | Product Dimension(mm)
Te=-10℃, Tsuc=18℃, Ta=32℃ | Te=-30℃, Tsuc=18℃, Ta=32℃
3PH 380V 50Hz | 6.0 HP | R448A/R404A/A2L | 9350 | 4550 | -40～-5 | ZSI18KQE or ZF18KQE | 1015*420*1250

2-13 HP R448A/R404A/A2L LBP Fixed Frequency 380V Outdoor Refrigeration Unit
? Model | BYGF-020-ZSL-SMDP | BYGF-030-ZSL-SMDP | BYGF-040-ZSL-SMDP | BYGF-050-ZSL-SMDP | BYGF-060-ZSL-SMDP | BYGF-075-ZFL-SMDP | BYGF-080-ZFL-RMDP | BYGF-100-ZFL-RMDP | BYGF-130-ZFL-RMDP
Power Supply | 3PH 380V 50Hz
HP Compressor | 2 HP | 3 HP | 4 HP | 5 HP | 6 HP | 7.5 HP | 8 HP | 10HP | 13HP
Refrigerant | R449A / R448A / R454C / R455A / R404A
Evap. Temp.(℃) | -20～10
Ambient Temp.(℃) | -15～48
Compressor Model | ZSI? Series | ZSI06KQE | ZSI09KQE | ZSI11KQE | ZSI15KQE | ZSI18KQE | / | / | / | /
ZF Series | ZF06KQE | ZF09KQE | ZF13KQE | ZF15KQE | ZF18KQE | ZF25KQE | ZFI36KQE | ZFI50KQE | ZFI59KQE
Product Dimension(mm) | 1015*420*850 | 1015*420*1250 | 1200*490*1250 | 1000*810*1230 | 1400*810*1230
Installation Dimension(mm) | 580*385 | 640*440 | 450*760 | 900*760

R449A Cooling
Capacity（W）

Evap. Temp.(℃)

Test Conditions：GB/T 21363-2018??? Ambient Temp.:32℃?? Subcooling Temp.:0℃?? Suction Temp.:18℃

-40 | 920 | 1250 | 1700 | 2200 | 2700 | 3200 | 4700 | 6550 | 7950
-35 | 1160 | 1550 | 2100 | 2800 | 3400 | 3900 | 5750 | 7700 | 9400
-30 | 1410 | 2100 | 2600 | 3750 | 4550 | 4800 | 7000 | 9300 | 11300
-25 | 1710 | 2350 | 3150 | 4200 | 5050 | 5850 | 8300 | 11300 | 14400
-20 | 2090 | 3100 | 4250 | 5600 | 6600 | 7800 | 10650 | 14850 | 18100
-15 | 2570 | 3600 | 5150 | 6700 | 7900 | 9250 | 12550 | 17450 | 21350
-10 | 3120 | 4400 | 6250 | 8000 | 9350 | 10800 | 14850 | 20450 | 24600
-5 | 3720 | 5200 | 7550 | 9450 | 11150 | 12450 | 16700 | 23300 | 27900